- Factory-made, quality-controlled and tested to stringent ASTM standards
- Highly-resistant to chemicals and offers excellent abrasion- and scratch-resistance properties
- Available in industry-standard DR 35 and DR 41
The need for a durable and cost-efficient pipe rehabilitation solution has never been more paramount. The engineers at IPEX recognized this need and have responded with NovaForm PVC Liner, a product that brings the lasting benefits of factory-made PVC pipe to the North American trenchless pipe rehabilitation industry.
Size Range 6" – 30" (150mm – 750mm)
Dimensional Ratio (DR) 35, 41
This specification covers requirements and test methods for materials, dimensions, workmanship, flattening resistance, impact resistance, pipe stiffness, extrusion quality, marking and packaging.
The pipe shall be made from PVC compound meeting all the requirements for cell classification 12111 as defined in specification D1784 and with minimum physical properties:
Tensile Strength Test Method D638 3,600psi (25MPa)
Tensile Modulus Test Method D638 155,000psi (1069MPa)
Flexural Strength Test Method D790 4,100psi (28MPa)
Flexural Modulus Test Method D790 145,000psi (1000MPa)
Heat Deflection Temperature
(tested @ 264psi) Test Method D648 115°F (46°C)
Pipe FlatteningThere shall be no evidence of splitting, cracking or breaking when the rounded pipe is tested according to section 11.3 of ASTM F1871.
In the early 1980s, decision makers in charge of the City of Vaudreuil-Dorion infrastructures had a sense of vision and made a responsible choice for the lasting benefit of the tax payers. A vision that would ensure durable infrastructures for over 30 years. The technical services, in cooperation with the public works department, decided a major shift for products to be used in potable water distribution applications. Since then PVC has become ``The Material of Choice`` made by the City to meet the overall needs, taking into account the existing soil conditions throughout the territory.