- Suitable for exposed, concrete encased & direct burial
- Concrete tight in all weather conditions
- Offers high impact and tensile strength
Scepter offers a comprehensive offering of PVC nonmetallic conduit fittings including adapters, couplings, elbows, access fittings, boxes, cover plates and expansion fittings virtually any fitting required to complete the PVC conduit system.
Easy installations, the ability to perform in demanding environments and labor savings are the reasons nonmetallic conduit fittings chosen by contractors. Scepter PVC conduit fittings offer both high impact and tensile strength, are nonconductive and are resistant to a wide range of chemicals such as acids, alkalis and salt solutions.
1/2" - 8" (12mm - 200mm)
CSA C22.2 No. 85
UL Listed UL514B - UL514C
Bridges & tunnels
Water treatment plants
Sewage treatment plants
Pulp & paper industries
Street & highway lighting
Food processing plants
All wiring shall be installed in Rigid PVC conduit and secured to PVC boxes and cabinets by means of proper fittings. All boxes, access fittings and covers shall be furnished with threaded brass inserts, brass screws and PVC gaskets. Rigid PVC fittings and junction boxes shall be used for all outlets, pull boxes and junction points. All PVC junction boxes shall be NEMA 1, 2, 3, 4, 4X, 6P, 12 and 13 rated and UL Listed for wet locations.
Exposed conduit shall be securely held in place by suitable hangers or straps with the maximum spacing of points for supports not exceeding those specified in the CEC or NEC. Except when embedded in concrete, rigid conduit pipe shall not be clamped tightly. It shall be supported in such a manner as to permit adequate linear movement, allowing for expansion and contraction of conduit due to temperature change. Where a temperature change exceeding 25°F (14°C) is anticipated, rigid PVC expansion joints shall be installed in accordance with the manufacturer’s recommendations.
Proper care shall be taken when field bending, to maintain the internal diameter and wall thickness of the conduit. The contractor shall furnish and install Scepter Rigid PVC conduit pipe and fittings made by IPEX. Where the engineer’s specifications indicate Scepter products or equivalent, the equivalent shall be CSA certified and accepted by the Canadian Electrical Code. Due to broad manufacturing tolerances, all pipe and fitting products shall be of the same manufacturer.